Electric motors have many applications in residential, commercial and industrial settings. Due to their widespread use, motors represent over 45% of global electricity consumption. Industry associations like NEMA and IEC are aware of this, and they are constantly working on standards to improve motor efficiency.
- Higher efficiency motors can save thousands of dollars annually for building owners.
- Power companies can also reduce their operating costs, since the transmission and distribution burden on the grid is decreased.
- There is also an environmental benefit, since a large portion of the electricity supply still comes from fossil fuels.
As of August 2019, NEMA has three motor efficiency classes: Standard Efficiency, Energy Efficient and Premium Efficiency. On the other hand, IEC has four classes: IE1, IE2, IE3 and IE4. The first three classes under IEC standards are roughly equivalent to the three NEMA classes, while the IE4 class is called Super Premium Efficiency. These efficiency classes are specified in the IEC 60034-30-1 standard, and the latest version was published in 2014.
Find the best energy efficiency upgrades for your building and reduce power and gas bills.
The next version of the IEC standard will introduce the IE5 class, known as Ultra Premium Efficiency. Energy losses are reduced by 20% or more between classes, which means an IE5 motor will have a 20% loss reduction with respect to an equivalent IE4 motor. The Ultra Premium Efficiency class has not been specified in the standard yet, but some manufacturers have already developed motors that will be compliant.
Estimating the Savings from a Motor Upgrade
To get an accurate calculation of how much you can save with an equipment upgrade, an energy audit is the best option. However, the percentage savings from a motor replacement can be estimated with the following formula:
As an example, assume a motor with 85% efficiency is replaced with a unit that has 91% efficiency. Using the formula above, the savings value is 0.066 or 6.6%. If the existing motor was consuming 300,000 kWh per year, the new one will save 19,800 kWh. With an electricity price of 15 cents/kWh, this is equivalent to $2,970 in annual savings.
The dollar savings achieved with a motor upgrade will be determined by three main factors:
- The efficiency difference between the existing motor and the upgrade.
- The operating schedule of the motor.
- The local electricity tariff.
To maximize the return on investment from a motor upgrade, the best approach is starting with motors that have a low efficiency and a long operating schedule.
Enhancing the Savings from a Motor Upgrade with Speed Control
When motors are used intermittently, or at part-load during extended periods, speed controls provide a significant savings opportunity. Variable frequency drives (VFD) reduce the input voltage and frequency provided to a motor, lowering the RPM and power consumption. This control method is especially effective for ventilation and pumping systems, which tend to have a variable workload throughout the day.
Considerable energy savings are possible if motors are upgraded to the new IE5 Ultra Premium Efficiency class, and then equipped with VFDs. In the case of HVAC systems, a motor upgrade can achieve synergy with other measures such as chiller and boiler replacements.
When upgrading motors, a careful inspection of the wiring and electrical protections is strongly recommended. Motor upgrades are generally expensive projects, and protecting that investment is in the best interest of building owners. The power supply quality is also important to ensure that motors have a long service life, since they are vulnerable to issues like under-voltage and phase voltage imbalance. Electrical engineers can find issues that are affecting your installation, to then propose cost-effective solutions.