No matter how careful you may be, a fire can break out unexpectedly in any building and so effective fire alarm system as one of the building smart devices is paramount to ensure that the occupants of the building are entirely or partially evacuated to safety. Buildings are required by building codes to install fire alarm systems.
Now, which alarm system should you install? Effective from the 1st of July 1996, the American National Standard (ANSI) has adopted the internationally standardized evacuation signal, now popularly known as the temporal 3 pattern, in short as T3. This signal is in compliance with the standard ANSI S3.41 in America and ISO 8201, and it is referred to as the Audible Emergency Evacuation Signal by both standard organizations. Following its enactment, the NFPA (National Fire Protection Association) has enforced that all fire alarm systems to be installed after the 1st of July 1996 should utilize the temporal pattern. The conventional alarm systems with their constant audio signals can be modified to comply with the new building codes as highlighted by the NFPA 72 code.
How does the Temporal 3 Fire Alarm System work?
Unlike the traditional fire alarm systems that use constant alarm signals, the Temporal 3 (T3) Fire Alarm System uses a pulsed audio signal that is repeated after 180 seconds. How this works is that it has a tonal sequence that becomes ON for half a second and OFF for the next half a second which continues for three cycles in succession. It remains silent for 1.5 seconds during those cycles.
Some alarm system fail in their purposes mainly due to the poor audio or voice signals. NFPA 72 emphasizes the requirements of temporary 3 pattern that it should be distinctive and should not be used for other purposes other than fire notifications. Oftentimes, a fire notification can prompt various actions such as partial and complete evacuation. If a complete evacuation is required, then the T3 is highly required whereas for partial evacuation a voice-based signal is recommended to direct the building occupants to a safer place.
Equally important, the building occupants must be trained on how to interpret the T3 fire alarm systems. Others may hear the sound but fail to respond to the actions if training has not been provided. And to eliminate confusions that could arise in the failure of other alarm systems, the NFPA 72 code ensured that the temporal 3 fire alarm system remained relevant with society’s communication demands in fire detections.
Installing the Temporal 3 Fire Alarm Systems
For your fire protection needs, the T3 has to installed according to the standards set and the right locations. For instance, the detection device should be 4 inches from the ceiling supply such as fans and air diffusers and 10 inches from wall supplies such as air diffusers. Ideally, T3 alarm systems should be installed in locations that have combustible materials such as woods and plastics. Classrooms, work offices, corridors, halls, computer rooms, and many other storage areas should be prioritized when installing these alarm systems.
Do not forget the directory with all the emergency telephone numbers for relevant safety operators to be called by occupants should a fire break out. But, modern alarm systems come with smart control panels that serve as the brain behind the efficacy of the systems. For instance, the control panel can be programmed to automatically alert relevant authorities about the signaled fire. Meanwhile, the occupants will be able to vacate the building. Section 18.104.22.168 of NFPA 72 editions in 2010 and 2013 requires that the basic frequency of temporal 3 fire alarm systems should be of 520 Hz frequency so it can awaken the occupants of the building.
Benefits of the Temporal 3 Fire Alarm Systems
Temporal 3 Fire Alarm Systems are automatic controls that bear huge benefits for homeowners in their fire detection strategies. As already indicated, some people fall victim to fire damages due to the failure to respond to alarm signals and that failure is attributed to the alarm system’s inaudibility or distorted voice signals. Temporal 3 fire alarm systems prevent such inconveniences with their unique pulsed audio signals hence the NFPA enforces that buildings should have them. The NFPA 72 code also reinforces the requirements for mass notifications in weather emergencies, chemical emergencies, and many more threats.
Temporal 3 Fire Alarm Systems versus Voice-Evac Systems
You may ask if it is possible to use both the Voice-Evac and the Temporal 3 Systems. These systems have different prompts and as thus could cause confusions if used simultaneously. For instance, the temporal 3 systems may prompt the occupant to vacate the building completely while the voice-evacuation systems prompt the occupants to relocate to a different region. Voice-Evac systems are pre-recorded in real time to offer commands. To install them in a building, especially a multi-storey building, there must be speakers at every level to notify all the tenants. Typically, there is an audio amplifier credited to the voice commands. However, the temporal pattern may be installed as a backup should the voice-evacuation fail to send the signals.
Installing fire alarm systems and automatic sprinklers in buildings has become a standard of all buildings to ensure the safety of the occupants. While there is a plethora of alarm systems from smoke detectors to heat detectors, the NFPA has set standards to be complied with when installing fire alarm systems.
The temporal 3 fire alarm system enacted as the standard on 1 July 1996. Therefore, all alarm systems installed thereafter should have this system. The old systems can also be modified to comply with the building codes and NFPA 72 requirements. The temporal 3 fire alarm system operate in pulses with some silences in between to alert the occupants should there be a fire.